@prefix bf: <https://brickschema.org/schema/1.0.2/BrickFrame#> .
@prefix bldg: <http://buildsys.org/ontologies/MSC#> .
@prefix brick: <https://brickschema.org/schema/1.0.2/Brick#> .
@prefix brick1: <https://brickschema.org/schema/1.1/Brick#> .
@prefix brick_v_1_0_2: <https://brickschema.org/schema/1.0.2/Brick#> .
@prefix brickframe: <https://brickschema.org/schema/1.0.2/BrickFrame#> .
@prefix btag: <https://brickschema.org/schema/1.0.2/BrickTag#> .
@prefix owl: <http://www.w3.org/2002/07/owl#> .
@prefix rdf: <http://www.w3.org/1999/02/22-rdf-syntax-ns#> .
@prefix rdfs: <http://www.w3.org/2000/01/rdf-schema#> .
@prefix tag: <https://brickschema.org/schema/1.1/BrickTag#> .
@prefix xml: <http://www.w3.org/XML/1998/namespace> .
@prefix xsd: <http://www.w3.org/2001/XMLSchema#> .

bldg:AHU05 a brick1:Air_Handler_Unit ;
    brickframe:hasSite bldg:MSC ;
    brick1:hasPoint bldg:MSC.AHU.AHU05.Cooling_Valve_Output,
        bldg:MSC.AHU.AHU05.Heating_Valve_Output,
        bldg:MSC.AHU.AHU05.Mixed_Air_Temp,
        bldg:MSC.AHU.AHU05.Mode,
        bldg:MSC.AHU.AHU05.Outside_Air_Temp,
        bldg:MSC.AHU.AHU05.Outside_Air_Temp_Virtual,
        bldg:MSC.AHU.AHU05.Return_Air_Temp,
        bldg:MSC.AHU.AHU05.Supply_Air_Temp,
        bldg:MSC.AHU.AHU05.Supply_Air_Temp_Setpoint ;
    brick1:isFedBy bldg:chiller .

bldg:AHU06 a brick1:Air_Handler_Unit ;
    brickframe:hasSite bldg:MSC ;
    brick1:hasPoint bldg:MSC.AHU.AHU06.Cooling_Valve_Output,
        bldg:MSC.AHU.AHU06.Heating_Valve_Output,
        bldg:MSC.AHU.AHU06.Mixed_Air_Temp,
        bldg:MSC.AHU.AHU06.Mode,
        bldg:MSC.AHU.AHU06.Outside_Air_Temp_Virtual,
        bldg:MSC.AHU.AHU06.Return_Air_Temp,
        bldg:MSC.AHU.AHU06.Supply_Air_Temp,
        bldg:MSC.AHU.AHU06.Supply_Air_Temp_Setpoint ;
    brick1:isFedBy bldg:chiller .

bldg:AHU07 a brick1:Air_Handler_Unit ;
    brickframe:hasSite bldg:MSC ;
    brick1:hasPoint bldg:MSC.AHU.AHU07.Cooling_Valve_Output,
        bldg:MSC.AHU.AHU07.Heating_Valve_Output,
        bldg:MSC.AHU.AHU07.Mode,
        bldg:MSC.AHU.AHU07.Outside_Air_Temp_Virtual,
        bldg:MSC.AHU.AHU07.Return_Air_Temp,
        bldg:MSC.AHU.AHU07.Supply_Air_Temp,
        bldg:MSC.AHU.AHU07.Supply_Air_Temp_Setpoint ;
    brick1:isFedBy bldg:chiller .

brick_v_1_0_2:Ambient_Illumination_Sensor a owl:Class ;
    rdfs:subClassOf brick_v_1_0_2:Illumination_Sensor .

brick_v_1_0_2:Green_Button_Meter a owl:Class ;
    rdfs:subClassOf brick_v_1_0_2:Building_Electric_Meter .

brick_v_1_0_2:PlugStrip a owl:Class ;
    rdfs:subClassOf brick1:Equipment .

brick_v_1_0_2:RTU a owl:Class ;
    rdfs:subClassOf brick1:AHU .

brick_v_1_0_2:Thermostat_Mode_Command a owl:Class ;
    rdfs:subClassOf brick1:Command .

brick_v_1_0_2:Thermostat_Status a owl:Class ;
    rdfs:subClassOf brick1:Status .

brickframe:areaSquareFeet a owl:ObjectProperty ;
    rdfs:range brickframe:Label .

brickframe:areaSquareMeters a owl:ObjectProperty ;
    rdfs:range brickframe:Label .

brickframe:humanName a owl:ObjectProperty ;
    rdfs:range brickframe:Label .

brickframe:isSiteOf a owl:ObjectProperty ;
    rdfs:domain brick_v_1_0_2:Site ;
    owl:inverseOf brickframe:hasSite .

brickframe:numFloors a owl:ObjectProperty ;
    rdfs:range brickframe:Label .

brickframe:primaryFunction a owl:ObjectProperty ;
    rdfs:range brickframe:Label .

brickframe:timezone a owl:ObjectProperty ;
    rdfs:range brickframe:Label .

brickframe:zipCode a owl:ObjectProperty ;
    rdfs:range brickframe:Label .

bldg:MSC.AHU.AHU05.Cooling_Valve_Output a brick1:Cooling_Command,
        brick1:Valve_Command ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU05.Cooling Valve Output" ;
    brickframe:uuid "1d072ba6-93c6-3a8f-8b29-148cf8fb590c" .

bldg:MSC.AHU.AHU05.Heating_Valve_Output a brick1:Command ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU05.Heating Valve Output" ;
    brickframe:uuid "673f86f7-863e-384b-8feb-edaa274c785a" .

bldg:MSC.AHU.AHU05.Mixed_Air_Temp a brick1:Mixed_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU05.Mixed Air Temp" ;
    brickframe:uuid "28ecfeae-16d1-3cbf-b923-eb3e8676017f" .

bldg:MSC.AHU.AHU05.Mode a brick_v_1_0_2:Mode ;
    brickframe:pointname "MSC.AHU.AHU05.Mode" ;
    brickframe:uuid "b3e31e5f-a4f7-3a29-98b9-34d25dd00d6e" .

bldg:MSC.AHU.AHU05.Outside_Air_Temp a brick1:Outside_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU05.Outside Air Temp" ;
    brickframe:uuid "b909188c-584a-3a48-b6ab-abb33f8b269e" .

bldg:MSC.AHU.AHU05.Outside_Air_Temp_Virtual a brick1:Outside_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU05.Outside Air Temp Virtual" ;
    brickframe:uuid "e1ab92e7-8a36-36f0-b548-a3153fa0fac0" .

bldg:MSC.AHU.AHU05.Return_Air_Temp a brick1:Return_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU05.Return Air Temp" ;
    brickframe:uuid "027e1914-e4fe-3595-b28a-d39cd7404266" .

bldg:MSC.AHU.AHU05.Supply_Air_Temp a brick1:Supply_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU05.Supply Air Temp" ;
    brickframe:uuid "b89ce9a5-2a02-3836-8efb-00d66feb1e86" .

bldg:MSC.AHU.AHU05.Supply_Air_Temp_Setpoint a brick_v_1_0_2:Supply_Air_Temperature_Setpoint ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU05.Supply Air Temp Setpoint" ;
    brickframe:uuid "7fdc3350-c61e-311b-b40b-58ffca71e959" .

bldg:MSC.AHU.AHU06.Cooling_Valve_Output a brick1:Cooling_Command,
        brick1:Valve_Command ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU06.Cooling Valve Output" ;
    brickframe:uuid "dadb1e73-857c-3e05-ad8d-d1f9075756d5" .

bldg:MSC.AHU.AHU06.Heating_Valve_Output a brick1:Command ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU06.Heating Valve Output" ;
    brickframe:uuid "c5c7f978-e4ae-34f5-8502-ebae91.0.299" .

bldg:MSC.AHU.AHU06.Mixed_Air_Temp a brick1:Mixed_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU06.Mixed Air Temp" ;
    brickframe:uuid "8827d4f4-2498-3ab9-aabd-8c40b50bed3e" .

bldg:MSC.AHU.AHU06.Mode a brick_v_1_0_2:Mode ;
    brickframe:pointname "MSC.AHU.AHU06.Mode" ;
    brickframe:uuid "daa1baf5-31aa-3a57-82b2-092c6c786c25" .

bldg:MSC.AHU.AHU06.Outside_Air_Temp_Virtual a brick1:Outside_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU06.Outside Air Temp Virtual" ;
    brickframe:uuid "c6692eca-a29b-3831-9b2d-89d556bfb452" .

bldg:MSC.AHU.AHU06.Return_Air_Temp a brick1:Return_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU06.Return Air Temp" ;
    brickframe:uuid "516a413c-f7ac-32b3-bf66-3b9e7f74b113" .

bldg:MSC.AHU.AHU06.Supply_Air_Temp a brick1:Supply_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU06.Supply Air Temp" ;
    brickframe:uuid "08267052-7a27-35b3-bb06-344a897b55e4" .

bldg:MSC.AHU.AHU06.Supply_Air_Temp_Setpoint a brick_v_1_0_2:Supply_Air_Temperature_Setpoint ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU06.Supply Air Temp Setpoint" ;
    brickframe:uuid "5c621bb0-e067-39d2-8f3c-cbae857fbf99" .

bldg:MSC.AHU.AHU07.Cooling_Valve_Output a brick1:Cooling_Command,
        brick1:Valve_Command ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU07.Cooling Valve Output" ;
    brickframe:uuid "980ee9c1-7aa0-309c-b5c8-ee97f57fa1a5" .

bldg:MSC.AHU.AHU07.Heating_Valve_Output a brick1:Command ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU07.Heating Valve Output" ;
    brickframe:uuid "77e91827-8201-39c9-a3d4-1ecb39a639eb" .

bldg:MSC.AHU.AHU07.Mode a brick_v_1_0_2:Mode ;
    brickframe:pointname "MSC.AHU.AHU07.Mode" ;
    brickframe:uuid "eb9ededb-01.0.2e6c-b750-d4650813779e" .

bldg:MSC.AHU.AHU07.Outside_Air_Temp_Virtual a brick1:Outside_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU07.Outside Air Temp Virtual" ;
    brickframe:uuid "38ebb5c4-fcb7-3176-bb92-ea6a98f5e319" .

bldg:MSC.AHU.AHU07.Return_Air_Temp a brick1:Return_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU07.Return Air Temp" ;
    brickframe:uuid "eed08e8a-edea-3f1a-ace0-32e27e0c0d5d" .

bldg:MSC.AHU.AHU07.Supply_Air_Temp a brick1:Supply_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU07.Supply Air Temp" ;
    brickframe:uuid "c4c03635-48ad-3631-84ec-5cbf9b0a2d89" .

bldg:MSC.AHU.AHU07.Supply_Air_Temp_Setpoint a brick_v_1_0_2:Supply_Air_Temperature_Setpoint ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.AHU.AHU07.Supply Air Temp Setpoint" ;
    brickframe:uuid "ebe7e67e-fc1d-3fa5-bf7d-232028e903e9" .

bldg:MSC.CHW.Building_Chilled_Water_Flow a brick_v_1_0_2:Chilled_Water_Flow_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.CHW.Building Chilled Water Flow" ;
    brickframe:uuid "0caa409c-f994-3193-a29e-2b16baf754cb" .

bldg:MSC.CHW.Building_Chilled_Water_Return_Temp a brick1:Chilled_Water_Return_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.CHW.Building Chilled Water Return Temp" ;
    brickframe:uuid "d995e072-13d9-38ce-925a-42f54444ff98" .

bldg:MSC.CHW.Building_Chilled_Water_Supply_Temp a brick1:Chilled_Water_Supply_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.CHW.Building Chilled Water Supply Temp" ;
    brickframe:uuid "3425e8cb-8768-39ae-8a5b-10014cc4f5d4" .

bldg:MSC.CHW.Building_Chilled_Water_Supply_Temp_Setpoint a brick_v_1_0_2:Chilled_Water_Supply_Temperature_Setpoint ;
    brickframe:pointname "MSC.CHW.Building Chilled Water Supply Temp Setpoint" ;
    brickframe:uuid "81022323-608d-337f-9e9c-40dd1c08c86f" .

bldg:MSC.CHW.ECONOMIZER a brick1:Damper_Position_Command ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.CHW.ECONOMIZER" ;
    brickframe:uuid "d908cb9f-ff5b-350f-a824-bd800243699e" .

bldg:MSC.CHW.Loop_Chilled_Water_Return_Temp a brick1:Chilled_Water_Return_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.CHW.Loop Chilled Water Return Temp" ;
    brickframe:uuid "d08745c8-7695-3795-aab3-729545aa2db8" .

bldg:MSC.CHW.Loop_Chilled_Water_Supply_Temp a brick1:Chilled_Water_Supply_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.CHW.Loop Chilled Water Supply Temp" ;
    brickframe:uuid "1f47ae11-0a48-3584-9f7b-9501c76ab104" .

bldg:MSC.CHW.Outside_Air_Temp a brick1:Outside_Air_Temperature_Sensor ;
    brickframe:hasSite bldg:MSC ;
    brickframe:pointname "MSC.CHW.Outside Air Temp" ;
    brickframe:uuid "9e06aad7-ee48-31c0-9f1a-29f9b3028298" .

brick_v_1_0_2:Building_Electric_Meter a owl:Class ;
    rdfs:subClassOf brick_v_1_0_2:Electric_Meter .

brick_v_1_0_2:Illumination_Sensor a owl:Class ;
    rdfs:subClassOf brick1:Sensor .

brickframe:hasSite a owl:ObjectProperty ;
    rdfs:range brick_v_1_0_2:Site .

bldg:chiller a brick1:Chiller ;
    brickframe:hasSite bldg:MSC ;
    brick1:hasPoint bldg:MSC.CHW.Building_Chilled_Water_Flow,
        bldg:MSC.CHW.Building_Chilled_Water_Return_Temp,
        bldg:MSC.CHW.Building_Chilled_Water_Supply_Temp,
        bldg:MSC.CHW.Building_Chilled_Water_Supply_Temp_Setpoint,
        bldg:MSC.CHW.ECONOMIZER,
        bldg:MSC.CHW.Loop_Chilled_Water_Return_Temp,
        bldg:MSC.CHW.Loop_Chilled_Water_Supply_Temp,
        bldg:MSC.CHW.Outside_Air_Temp .

brick_v_1_0_2:Site a owl:Class ;
    rdfs:subClassOf brick1:Location .

bldg:MSC a brick_v_1_0_2:Site ;
    brickframe:AreaSquareFeet "16618" ;
    brickframe:Country "US" .

